Mutiple Mode Hybrid PV Energy Storage Grid Solar Inverter
HT series is a new hybrid PV energy storage inverter controller integrating PV energy storage,mains charging
and storage and AC sine wave output. Using DSP control through advanced control algorithms, it comes with high
response speed, high reliability, high industrialization standard and other characteristics.
Four charging modes are available: only PV, mains priority, PV priority, and hybrid charging by mains & PV;
two output modes: inverter and mains are available to meet different application needs.
1. Full digital voltage; current double closed loop control, combined with advanced SPWM technology to output
pure sine wave.
2. Two output modes and 4 charging modes are available for choice.
3. AdvancedMPPT technology with efficiency up to 99.9%.
4. LCD screen design, with 3 LED indicators, for dynamic display of system data and run status; ON/OFF rocker
switch controls AC output.
5. Power saving mode reduces no-load loss.
6. Intelligent variable speed fan ensures efficient heat dissipation, and thereby extends system life.
7. Double lithium battery activation modes: mains and PV, and supports lead-acid battery and lithium battery
8. Multiple protections provide 360 ° all-round protection for the system. Complete protections include multi-electrical
appliance air switch short circuit protection, overvoltage and undervoltage protection, overload protection, back-flow
9. Horizontal installation facilitates cabinet combination installation.
10. Lithium battery can be activated by both mains and PV panel.
|Rated input voltage||220/230Vac||110/120Vac|
|Input voltage range||(170Vac~280Vac) ±2%
|Frequency range||47±0.3Hz ~ 55±0.3Hz (50Hz);
57±0.3Hz ~ 65±0.3Hz (60Hz);
|Conversion time||10ms (typical)|
|(bypass and inverter)|
|Maximum bypass overload current||40A|
|Output voltage waveform||Pure sine wave|
|Rated output power (VA)||3000(2600/2700
|Rated output power (W)||3000(2600/2700
|Rated output voltage (Vac)||230Vac(200/208/220/240Vac Settable)||120Vac(100/105/110Vac Settable)|
|Output voltage error||±5%|
|Output frequency range (Hz)||50Hz ± 0.3Hz
60Hz ± 0.3Hz
|Overload protection||(102%<load<125%) ±10%: Report error and turn off output after 5 minutes;
(125%<load<150%) ±10%: Report error and turn off output after 10 seconds;
Load>150% ±10%: Report error and turn off output after 5 seconds;
|(102%<load<110%) ±10%: Report error and turn off output after 5 minutes;
(110%<load<125%) ±10%: Report error and turn off output after 10 seconds;
Load>125% ±10%: Report error and turn off output after 5 seconds;
|Loaded motor capacity||2HP||3HP||4HP||1HP||2HP||2HP|
|Bypass circuit breaker specification||63A|
|Rated battery input voltage||48V (minimum starting voltage 44V)|
|Battery voltage range||40.0Vdc~60Vdc ± 0.6Vdc (undervoltage alarm / shutdown voltage / overvoltage alarm / overvoltage recovery...LCD screen can be set)|
|Eco mode||Load ≤ 50W|
|Maximum charge current||0-60A||0-40A|
|Charge voltage range||40 - 58Vdc||40 - 60Vdc|
|Circuit breaker specification||(AC IN) 63A/(BAT) 125A|
|Maximum PV open circuit voltage||145Vdc|
|PV operating voltage range||60-145Vdc|
|MPPT voltage range||60-115Vdc|
|Battery voltage range||40-60Vdc|
|Maximum output power||4200W|
|PV charge current range (settable)||0-80A|
|Charge short circuit protection||BAT circuit breaker and fuse|
|Wiring protection||Reverse polarity protection|
|Hybrid charging Max charger current specifications (AC charger+PV charger)|
|Max charger current(can be set)||0-140A||0-120A|
|EMC certification level||EN61000, C2|
|Operating temperature range||-15°C to 55°C|
|Storage temperature range||-25°C ~ 60°C|
|RH range||5% to 95% (conformal coating protection)|
|Heat dissipation||Forced air cooling, adjustable air speed|
Product Maintenance and Fault Handling:
|1||PV current/power limiting protection||When charging current or power of the PV array configured exceeds the PV rated, it will charge at the rated.|
|2||PV night reverse-current protection||At night, the battery is prevented from discharging through the PV module because the battery voltage is greater than the voltage of PV module.|
|3||Mains input over voltage protection||When the mains voltage exceeds 280V (230V model) or 140V (120V model), the mains charging will be stopped and switched to the inverter mode.|
|4||Mains input under
|When the mains voltage is lower than 170V (230V model /UPS mode) or 90V (120V model or APL mode), the mains charging will be stopped and switched to the inverter mode.|
|5||Battery over voltage protection||When the battery voltage reaches the overvoltage disconnection point, the PV and the mains will be automatically stopped to charge the battery to prevent the battery from being overcharged and damaged.|
|No display on the screen||Check if the battery air switch or the PV air switch has been closed;
if the switch is in the "ON" state; press any button on the screen to exit the screen sleep mode.
|Battery overvoltage protection||Measure if the battery voltage exceeds rated, and turn off the PV array air switch and Mains air switch.|
|Battery undervoltage protection||Charge the battery until it returns to the low voltage disconnection recovery voltage.|
|Fan failure||Check if the fan is not turning or blocked by foreign object.|
|Heat sink over temperature protection||When the temperature of the device is cooled below the recovery temperature, normal charge and discharge control is resumed.|
|Bypass overload protection, inverter overload protection||① Reduce the use of power equipment;
② Restart the unit to resume load output.
|Inverter short circuit protection||① Check the load connection carefully and clear the short-circuit fault points;
② Re-power up to resume load output.