|Phase:||10-20KVA: Single Phase; 20-100KVA: Three Phase||AC Input Voltage:||220V(one-phase) /380V(three Phase) ±25%|
|AC Input Frequency:||50/60Hz±10%||AC Input Power Factor:||0.95(with Input Filter)|
|Bypass Input Permitted Voltage Range:||220V(one-phase) /380V(three Phase) ±15%||OPutput Voltage:||220V±1%(steady Load) 220V±3%( Fluctuating Load)|
ups uninterruptible power supply,
ups unit power supply
Special Online Electricity UPS System Multiple Monitoring Zero Switch
CND310 system consists of electrical UPS, DBW bypass stablalized cabinet, and feeder cabinet of PDU series. CND310 is product that CONSNANT TECHNOLOGY CO., LTD, according to the requirement of China Power, designs exclusively for power plant, transformer substation, and distribution substation. It possesses on-line double conversion and zero switch function. It can be mainly applied for power system telemechanics, PTU, power line communication, power system monitoring and etc.. After being isolated and filtered by regulator, Single-phase 220V or three-phase 380V can provide stable power for load through inverter when the AC is normal. If the failure of AC power grid supply or a power cut occurs, direct current panel, the backup of power system, can invert to supply electricity through non-return diode. If the direct current panel is under voltage or cut off, static switch can shift to bypass stabilized cabinet to supply electricity. When the AC power becomes normal, the static switch automatically shift to AC power grid to supply electricity reversely. If the inverter is overloaded or the fault occurs to it, the static switch shift to bypass stabilized cabinet to supply electricity and indicates a warning signal at the same time.
Q: Could you do custom-made products?
A: Yes, please show us the drawing of the goods you need, or your requirement for the products, customized UPS is available.
Q: Can you print my picture or logo onto the products?
A: Yes, OEM and ODM accepted
Q: What included in the products?
A: It includes UPS unit, user manual, 2% free spares together with shipment for urgent issue. Test certificate(optional)
Q: Nobody in our company know how to install the UPS?
A: We can despatch engineer to assist you solve the problem if necessary(But you are requested to pay for the cost of ticket, hotel etc. ). Or you can despatch engineer(s) to our company to get training.
|Rating voltage||220V(one-phase) /380V(three phase)|
|Soft start||0-100% in 5”|
|Power factor||0.95(with input filter)|
|Permitted voltage range||±15%|
|Voltage accuracy||220V±1%(steady load) 220V±3%( fluctuating load)|
|Permitted Frequency range||50/60Hz±0.05Hz(powered by battery)|
|THD||Linearload<2%, non linear load<4%|
|Current crest ratio||3:1|
|Overload capacity||Normal in 110% load, 125% for 10min|
|Efficiency||Double switch:94%, ECO:98%|
|Maximum discharge current||36A||55A||73A||109A||145A||181A||218A||291A||364A|
|LCD||Chinese/English UPS status, operation instruction input voltage, output voltage, current, frequency, battery voltage, value of charge and discharge current, accident display, warning|
|Storage temperature||-25 ºC—55 ºC|